Reliable Heating and Air Conditioning Services in Brownsburg, Indiana
Give the Brownsburg HVAC experts a call today to request a free second opinion, a no-obligation estimate, or to book immediate heating or air conditioning services in Brownsburg, Indiana.
Full-Service Installations and Repairs to Meet Your HVAC Needs in Brownsburg, IN
Call Now to Request an Estimate or Schedule Trusted Heating and AC Services in Brownsburg, IN
At Family Heating & Air Conditioning, our goal is to help our neighbors find safe, efficient, and cost-effective solutions that will provide them with long-term comfort and peace of mind. No matter your needs, you can rely on our Brownsburg HVAC experts to provide you with honest professional advice, personalized solutions to meet your indoor comfort goals, and exceptional workmanship that will leave you with year-round comfort. Don’t hesitate to call on our Brownsburg heating and air conditioning team to discuss your needs and let us help you get your heating, AC, or air quality needs resolved without hassle.
Contact our Brownsburg HVAC experts today to schedule your next heating or cooling service in Brownsburg, IN or the surrounding area.
Contact Us Now!
for Brownsburg, IN
Great service! Helpful, courteous!
Gurka - Brownsburg, IN 46112
Jason R - Brownsburg, IN 46112
As always Family Heating and Air does a great job!
Great Service always!
Gurka - Brownsburg, IN 46112
Juan is courteous and knowledgeable!
REID - Brownsburg, IN 46112
Always great experience dealing with the staff from scheduling to the on-site technicians. Have used them for 10-15 years.
Charles - Brownsburg, IN 46112
B1 Clean & Check Service Cleaned and Tested heating system. Everything is working well at this time.
Replaced inducer. Everything working well at this time
Changed setting in thermostat and releveled. Inducer making some noise. Going to replace under warranty
Performed furnace tuneup. This is first visit on new contract. Rubber water supply tube from solenoid to humidifier assembly is torn. Homeowner elected to not replace line at this time, unhooked power supply to solenoid until replacement to ensure no water issues. If repair is made, water panel should be replaced. Bacteria growth and heavy particulates are active in ductwork- recommend installing air scrubber to improve indoor air quality. Blower wheel starting to accumulate buildup. System is currently functioning properly at this time. Passed carbon monoxide test at 0ppm. Www.airscrubberbyaerus.com
Performed B1 Furnace tuneup, this is first visit on new contract. Found blower wheel with significant buildup accumulating, no oil residue on motor or overamping is occuring currently. If left untreated, excess stress will be put on motor causing failure and loss of efficiency. Recommend advanced blower assembly pull/clean, upgrading filtration to polarized media filter and installing air scrubber to prevent reoccurance after cleaning. System is currently operating properly at this time, passed carbon monoxide test at 0ppm. www.airscrubberbyaerus.com
Performed fall tuneup on two systems. Carbon monoxide test passed at 0ppm on both. Main system for house has flame sensor tip cracked- currently is operational but recommend replacing before failure. Replaced flame sensor and verified proper operation at this time.
B2 Clean & Check Service Cleaned and tested heating system. Everything is working well at this time. Humidifier not running at this moment, it has a clogged drain line into the home.
Arrived on site to perform B2 fall tuneup. Found rust and oxidation on bottom of heat exchanger plates and intermittently throughout chamber. Found two holes while running inspection camera. Pulled blower and verified two cracks with separation. Furnace is unsafe to run with compromised heat exchanger. Furnace is 18 years old and outside of average lifespan. Blower motor has substantial buildup and has oil residue on casing. Turned off gas cock and advised not to operate until heat exchanger is replaced or new Furnace installed